Rule 61:15:07:04 Automatic sprinkler system requirements.
61:15:07:04. Automatic sprinkler system requirements. An
automatic sprinkler system must be installed in basements of school occupancies
when the total area of unseparated uses exceeds 1,500
square feet in floor area. All valves controlling the water supply for
automatic sprinkler systems must be electrically supervised when the number of
sprinkler heads exceeds 100. All automatic sprinkler systems must have a
water-flow switch which activates the building's fire alarm. For uses to be
considered as separated, the separation may not be less than as required for a
one-hour occupancy separation.
18 SDR 107, effective January 1, 1992.
Implemented:SDCL 13-25-3, 13-25-4.
Back to 61:15:07